
Support Technical and other questions related to the use of SuperBeam 

Thread Tools  Display Modes 
22nd October 2013, 07:24 PM  #1 
Member
Join Date: Sep 2013
Posts: 1

Correct inputting of loads
Sorry if this has been dealt with previously.
I have a floor joist system which supports roof loading as a point load. What is the correct method of inputting the loading if the floor joists are at 400mm centres for instance. I am getting conflicting advice. Do I times or divide the roof laoding by 0.4 (centres of the joists) to create the point load. Help/clarifcation would be appreciated. 
22nd October 2013, 10:10 PM  #2 
Administrator
Join Date: Apr 2008
Location: Melbourne, Australia
Posts: 822

Re: Correct inputting of loads
I'm not quite sure of the question. If you've got individual joists bearing on a trimmer etc at 400600c/s, such loads are treated as a UDL or part UDL (note that the loading in kN/m run so the general case load will be load/m2 x supported joist span/2. If this isn't what you've got can you explain in a little more detail please.
__________________
Tony Bryer, Greentram Software Pty Ltd 
23rd October 2013, 06:51 AM  #3 
Senior Member
Join Date: Apr 2011
Posts: 44

Re: Correct inputting of loads
If you have a floor joist which say takes a line load of studwork with say 2m of roof
loading would be udl floor 2.1 x 0.4 Point load stud 0.5 x 0.4 x 2.3 say for height of stud point load roof 1.66 x 0.4 x 2 the point load need to be positioned from one end probably not too clear 
23rd October 2013, 10:34 AM  #4 
Guest
Posts: n/a

Re: Correct inputting of loads
If I am understanding the question correctly you have a floor joist system spaced at 400c/c which is carrying roof loads which occur in a transverse direction to the span of the floor joists creating a series of point loads across the line of the joists. ( presumably there must also be a stud wall or other support member that transmits the load from the roof onto the floor joist which must also be accounted for)
But simply if the roof load is say 2.15kN/m run then when supported transversely by the floor joists at 400c/c then each individual point load on each joist will be = 2.15 x 0.4 = 0.86kN point loads. If you think about this you have 2.5 joists in every metre of floor width therefore 0.86 x 2.5 = 2.15kN/m Hope I have understood your question correctly. 
Thread Tools  
Display Modes  

